600V SUBMERSIBLE POWER CABLE WITH GROUND
TYPE TC-ER 2, 3 AND 4 CONDUCTOR
Cables are listed as “sunlight resistant” and are suitable for direct burial. The cables are intended to be used in aerial applications, tray, wire-ways, troughs, channels, duct and conduit in wet or dry applications.
Two, three or four conductors having TFFN or VW-1 THHN/THWN (PVC/ Nylon) conductors with PVC jacket conforming to Article 318 “Cable Trays” and Article 340 “Power and Control Cable Type TC”. Direct Burial, Passes 210,000 BTU flame test and suitable for use as submersible cable.
Conductors: Conductors consist of uncoated soft, copper strands meeting the requirements of ASTM B3. Unless otherwise specified, the conductor shall be supplied as Class B compressed per ASTM B8.
Insulation: The insulation is flame-retardant crosslinked polyethylene (XHHW-2) extruded concentrically over the conductor to the wall thickness for Type XHHW-2 as specified.
Conductor Coding: Phase identification is provided by number code on each insulated conductor.
Ground Wire: One stranded bare copper ground wire will be located in one of the outer interstices
Assembly: Conductors and ground wire are cabled together, “Filled” cables include suitable fillers with a binder to develop a round cable cross section.
Jacket: A protective sunlight and ozone resistant jacket of Polyvinyl Chloride (PVC) or chlorinated polyethylene (CPE) is extruded overall.
• Listed by UL as Type TC per Standard 1277 & IEEE 1202.
• Listed by UL as Type TC per Standard 1277 (4 AWG & larger, PVC jacketed only).
• Conforms to ICEA S-95-658/NEMA WC70 Non-shielded 0-2KV Cables
• Listed by UL as Sunlight Resistant
• Listed by UL as Direct Burial