ARMORED METHANE CABLE
600 VOLT 3 AND 4 CONDUCTOR
Aluminum Interlock Armored cable with overall PVC jacket is rated for use in Deep Well Submersible Methane Gas.
Conductors: The conductors consist of uncoated soft copper strands meeting the requirements of ASTM B-3. Unless otherwise specified the conductors are supplied as Class B compressed per ASTM B-8.
Insulation: The insulation is flame-retardant crosslinked polyethylene (XHHW-2) extruded concentrically over the conductor to the wall thickness for Type XHHW-2 as specified.
Conductor Coding: Phase identification is provided by number code on each insulted conductor.
Ground Wire: 80 mils (0.080 inches) (2.03mm) of heat and moisture resistant, polyvinyl chloride (PVC) integral filled inner jacket.
Assembly: 80 mils (0.080 inches) (2.03mm) of heat and moisture resistant, polyvinyl chloride (PVC) integral filled inner jacket.
Inner Jacket: Where specified an inner polyvinyl chloride (PVC) jacket is extruded over the assembly and under the protective armor.
Armor: Over the core assembly there is an interlocking armor of of either aluminum or galvanized steel as specified.
Jacket: A protective sunlight and ozone resistant jacket of polyvinyl chloride (PVC) is extruded for a tight fit over the interlocked armor.
UL 44: Thermoset-Insulated Wires & Cables
UL 159: Metal Clad Cables